System selection and mounting
in the course of structural health monitoring system design
In order to select structural health monitoring system components (SHM), it is necessary to perform a number of procedures, which will help to choose the suitable digital sensors, their quantity, and mounting areas:
- Define the controlled parameters and then select the particular SHM subsystems enabling control in accordance with the set requirements.
- Find out information on the number of floors and foundation’s square of the controlled object using corresponding design documentation.
- Define the necessary amount of the digital sensors to be included in the structural health monitoring system using the information from the clause «System components and controlled parameters».
- Mark digital sensors location for each of the levels (floors) of the controlled object (building).
When choosing digital sensor’s location it is necessary to take into consideration further cable connection.
If the building has 7 or fewer floors, the sensors are to be installed at the bottom part (at level/floor, which is as close to the foundation as possible) and at the top part (at the level/floor in direct vicinity to the ceiling). In the case of high structures, it is also necessary to select several intermediate floors for the control purposes in accordance with the information specified in the clause «System components and controlled parameters».
The modules placed inside of data acquisition nodes cabinets (interface converters, power supply sources and so on) are mounted on DIN-rails.
Each interface converter should be connected to industrial PC of the data acquisition node or (in the case if there are no PC-s in the structure of data acquisition nodes) to the SHM system server – for that purpose, Ethernet converters are used (the Ethernet converters have a corresponding amount of ports).
In the case if the Ethernet data transfer cable line length (from data acquisition nodes panels to the server) is less than 100 meters, it is possible to use Class 5 twisted pair. In the case of implementing longer cable lines, there should be used a fiber-optic cable with optical media-converters at both ends of the cable.